KL4510X1-EA1 | Emerson DeltaV | I.S. CHARM Address Terminal

2026-04-03T18:25:28+08:00

เวนเดอร์: Emerson
ประเภท: Terminal Block
ราคา: 66.00

Overview

The Emerson KL4510X1-EA1 is an Intrinsically Safe CHARM Terminal Block for the DeltaV electronic marshalling system. It provides safe field wiring connections for intrinsically safe CHARMs and is certified for hazardous area installations.

Technical Specifications

Product Type: I.S. CHARM Terminal Block

Part Number: KL4510X1-EA1

Field Circuit Power: +28 VDC at 45 mA

Ambient Temperature: -40 °C to +70 °C

Relative Humidity: 5–95% non-condensing

Shock Resistance: 10 g half-sine wave for 11 ms

Vibration Resistance: 1 mm peak-to-peak (2–13.2 Hz), 0.7 g (13.2–150 Hz)

Airborne Contaminants: ISA-S71.04–1985 Class G3

Certifications: ATEX, IECEx, FM, UKEX Zone 2

Installation Notes

Install on a compatible DeltaV CHARM base carrier

Do not insert or remove while energized in hazardous areas

Ensure proper grounding and shielding of field wiring

Follow Emerson DeltaV installation guidelines for I.S. CHARMs

Verify environmental compliance for temperature, humidity, and vibration